Vendor Case Study: Berner Air Curtains
Engineers’ Novel Rollup Doors Retrofit with Air Doors Stops Plant’s Flying Insect Ingress
When federal and international sanitary inspections mandated flying insect infiltration reductions at a California pharmaceutical manufacturing plant’s four shipping doors, project engineers started thinking far outside the box to save the facility more than $75,000 in necessary door retrofit costs.
The inspectors’ retrofit suggestions included replacing the 200,000-square-foot complex’s ineffective and difficult to clean doorway strip curtains with air curtains, which are used in a variety of door applications to eliminate insect infiltration from industrial complex doorways to restaurant drive-through windows.
Initially there were many design obstacles; however, the estimated $75,000 cost of modifying the four doorways’ rollup door mechanisms appeared to be an almost insurmountable challenge, according to Tyson Crowell, P.E., – project director and biopharmaceutical technology leader, Yonkers Industries, Cary, N.C. – a key construction partner for international biotech and pharmaceutical manufacturers that the building owner hired to solve the challenge.
Rollup doors are rarely combined with air curtains in retrofits because they both compete for the same strategic space directly above the door opening. Air curtain efficacy is greatest when mounted directly above the interior side of the doorway to discharge air down across the opening and meeting the floor slightly outside the threshold. The best alternative was raising and lengthening the rollup door mechanisms 28 inches to accommodate the 15 (h) x 18 (w)-inch air curtains on the 10-foot-high door openings at a cost of $75,000 in labor and materials in addition to the air curtains cost.
Additional costs also would be incurred from lost production and door use downtime. Any rollup door modification would require sealing the open door while modifying or relocating the rollup mechanism, a process that would take days and postpone the doorway’s services.
“The cost was important, but more critical was the fact we couldn’t afford any downtime whatsoever for the rollup doors.”
– Crowell, project director for Yonkers’ West Coast Operations, Walnut Creek, Calif.
Instead, Crowell and Van Sintchak, vice president of operations and energy recovery consultant at Nor-Cal Reps, Inc., Carson City, Nev., working with conceived the novel solution of allowing the rollup doors to remain untouched and usable while installing the air curtains.
The duo designed angle iron supports to mount air curtains by Berner International, New Castle, Pa., two feet outward from the rollup door. The air curtains are rotated 90-degrees with the air discharge facing the top of the doorway. To redirect the air discharge toward the floor, an aluminum air discharge plenum nozzle extension stretches 18-inches toward the wall, under the rollup door mechanism and angles 90-degrees downward at the top of the door opening.
Six Industrial Direct Drive 12 model air curtains (IDC 12) were outfitted with the plenum design to protect the one 11-foot-wide; one 13-foot-wide; and two 20-foot-wide door openings, the latter which required two 11-foot-wide air curtains each.
Dave Johnson, Berner International’s director of engineering and a source Crowell had used on dozens of other industrial air curtain projects, custom-designed, built, and tested the plenum idea. The 16-ga. (0.050) aluminum plenum has a 3-1/2-inch wide opening and stretches across the width of each air curtain. Also, an internal turning vane was installed at the 90-degree turn to eliminate the potential of turbulence and to help the adjustable discharge vanes that are used to direct the air stream. Air curtains were specified that offset a small additional static pressure created by the plenum nozzle extension. Johnson then used hot wire anemometer lab testing to assure the air curtain velocities and uniformity were sufficient to protect the door openings.
Once mounted, no adjustments were needed, because the volume, velocity, and uniformity of the air discharge performed exactly to specifications, according to post-installation site tests performed by Sintchak.
Besides $75,000 in savings, there was no downtime for the doors and the plenum modifications raised the air curtain costs only by a nominal 10-percent. Although no data has been collected, insect infiltration is minimal and well within GMP standards, according to Crowell.
Sintchak, who recently won Berner International’s inaugural “Innovation Award” for the project, concluded:
“This project’s success is really attributed to engineers thinking outside the box…as a matter of fact, two feet outside the air curtain box.”